Specifications of guaranteed power complexes
|Power, kW||Defined by the quantity of modules|
|МВЭУ ТТ 0,2||0,2-1,2|
|МВЭУ ТТ 1,0||1,0-2,0|
|МВЭУ ТТ 5,0||5,0-10,0|
|Power of one module, kW|
|МВЭУ ТТ 0,2||0,2|
|МВЭУ ТТ 1,0||1,0|
|МВЭУ ТТ 5,0||5,0|
|Output voltage of the complex, V||230 or 400/230||Defined by the requirement specification|
|Output voltage frequency,Hz||50±0,1|
|Wind speed in the operating range of МВЭУ ТТ, m / s||3,5-50|
|Design wind speed, m/s||12|
|Maximum design wind speed, m / s||45,60||Defined by the requirement specification|
|No wind and sun operation time||30 min- 2 days||Defined by the requirement specification and quantity of accumulators|
|Rack height, m||4|
|Noise level, dBA||not more than 45|
Specifications of ММВСДКГЭ «Windec» on modules of МВЭУ ТТ-5
|The quantity of modules||1||2||4||6|
|Sun battery power*, kW||5||10||20||30|
|Diesel generator power, kW||10||20||40||60|
|The quantity of accumulators*, pcs.||8-64||16-128||16-128||32-256|
|Total power of the sources, kW||17||30||70||95|
|The noise level, dBA, not more||45||45||45||45|
|* Wind power generation per year, kWh|
|5 m/s, kWh||4683||9366||18732||28098|
|6 m/s, kWh||7413||14826||29652||28098|
|7 m/s, kWh||11359||22718||45436||68154|
|8 m/s, kWh||16253||32506||65012||97518|
|12 m/s, kWh||30905||61810||123620||185430|
|Energy generation by a solar installation per year **, kWh||2500||5000||10000||18000|
|Fuel economy, %||8-35||8-35||8-35||8-35|
*defined by requirement specification.
*defined by wind and solar activity.
Guaranteed power complexes on modular wind turbine-type installations (МВЭУ TT), solar batteries and backup power supply from diesel generators are designed for uninterrupted power supply of industrial facilities of various purposes remote from centralized power lines.
The power supply facilities may include: gas pumping stations, compressor stations, water supply complexes, small enterprises, agricultural farms, settlements, technical surveillance points, military towns, aerodromes, coastal navigation systems, base cellular stations, ground stations of the Glonass operation system, and other civil and military purpose facilities.
Advantage of modular wind plants of the turbine type:
– wind plants have a modular design. One module can be placed on the other. Thus, the installed capacity on one rack will increase. From the point of view of the stability of the structure the most rational solution is the installattion, consisting of two modules with a total capacity of 10 kW.
– absence of current collectors;
– absence of systems of orientation to the wind, which allows them to work in the conditions of constantly changing winds in the direction;
– high reliability due to the strength of the design and the independence of the power supply of one module from another with multi-module construction.